This technical note shows the steps for Triconex ESD network setup for redundant ModbusTCP communications with a pair of DeltaV ModbusTCP VIMs.
Triconex PLC can be configured with two TCM cards for redundant communications with ModbusTCP VIMs. For communication effectiveness, there are certain configuration parameters that need to be in place.
Using the Triconex TriStation application, open Tricon Controller and double-click on Configuration to display configuration parameters.
Click on TCM module to display its properties.
On the Network tab select 10 Mbps Half Duplex or Auto-Negotiate for both Left and Right TCM cards. Note that the VIMs communicate at 10Mbps Half Duplex. Alternatively, an Auto-Negotiate switch can be used between the VIMs and the TCM network ports.
Specify the IP address for both Left and Right TCM cards. In the following display, we are using NET 1 for the VIM communications.
Select the Modbus TCP tab and configure the Port Selection and Port Settings as shown below. In the Port Selection list, 16 ports can be configured. It is recommended that all 16 ports be configured. For each Port number, specify the IP address of the VIM as shown in the Port Settings group below. Configure the first 8 Port numbers (1-8) for VIM-A, and the remaining 8 Port numbers (9-16) for VIM-B.
By specifying an IP address, only the VIM with the given IP address will be able to communicate with this TCM. Multiple Port numbers allow multiple Ethernet connections to become available. This is a requirement for the VIMs, which open multiple network connections with each TCM. With 8 ports configured with the IP address of VIM-A, and 8 ports configured with IP address of VIM-B, both of the VIMs will be able to communicate with each TCM card as required in a redundant setup.
Lastly, duplicate this configuration for the Right TCM card. Both Left and Right TCM cards must have the same configuration.
The Triconex network interfaces do no change IP addresses when a switchover is required, i.e., the same network address is always assigned to the same network card. To configure this behavior for the field device, select "Redundancy with No Switching IP" when configuring the device under the port in VIMNet Explorer, as shown in the screenshot below.
MYNAH Technologies LLC
390 South Woods Mill Road, Suite 100
Chesterfield, MO 63017 USA
© MYNAH Technologies 2012 - 2019. All rights reserved.
Designs are marks of MYNAH Technologies, Emerson Process Management, DeltaV, and the DeltaV design are marks of one of the Emerson Process Management of companies. All other marks are property of their respective owners. The contents of this publication are presented for informational purposes only, and while every effort has been made to ensure their accuracy, they are not to be construed as warrantees or guarantees, expressed or implied, regarding the products or services described herein or their use or applicability. All sales are governed by our terms and conditions, which are available on request. We reserve the right to modify or improve the design or specification of such products at any time without notice.
While this information is presented in good faith and believed to be accurate, Mynah Technologies does not guarantee satisfactory results from reliance upon such information. Nothing contained herein is to be construed as a warranty or guarantee, express or implied, regarding the performance, merchantability, fitness or any other matter with respect to the products, nor as a recommendation to use any product or process in conflict with any patent. Mynah Technologies reserves the right, without notice, to alter or improve the designs or specifications of the products described herein.