The following release notes are for the Ethernet/IP VIM v3.6.1
These release notes are for changes made to the Ethernet/IP VIM firmware for v3.6.1. The previous general released firmware version is v3.5.4. The flash procedure is documented in the product manual.
This firmware release is RECOMMENDED for all Ethernet/IP VIM firmware v3.5.x users. It is MANDATORY for all Ethernet/IP VIM users at or prior to firmware v3.3.64.
1. Dataset scan request/response time has been improved significantly through optimization of Ethernet/IP stack message handling resources.
2. Two new Special Data 5 flags (highlighted in table below) have been added to support redundant communications to a ControlLogix PLC where one network connection is to an ENBT or EN2T card, while the second network connection is directly to the PLC CPU channel 0 port via an Ethernet/IP to Serial converter like the 1761-NET-ENI module. Respectively, where the first network connection requires a path specification, the second does not. The Special Data 5 flags inform the VIM regarding which connection is pathless. The flags are as follows. A bit set to 1 implies an asserted flag, and flag values may be added to assert more than one flag. Unspecified flags are reserved.
|Special Data 5 Bit #||Value||Description|
|0||1||Read Inputs before sending outputs on output with readback dataset|
|1||2||Use DH+ commands in UCMM (encapsulated DF1) message structure|
|2||4||The Primary network connection uses a 1761-NET-ENI converter. A CPU path is not required for this connection.|
|4||8||The Secondary network connection uses a 1761-NET-ENI converter. A CPU path is not required for this connection.|
|8||256||For Boolean and Discrete output datasets - this flag forces the bits to be packed into bytes before being sent to the PLC. Normal functionality is one bit per byte.|
|9||512||Forces an output data write regardless of change pending.|
|10||1024||When specified, the first 4 16-bit words of the output dataset are used for communication status. On loss of communication, the ControlLogix fills these words with all bits set.|
3. Modified UCMM (Encapsulated DF1) message structure to support communication with DH485 devices via the DataLink GW1000 Gateway.
4. Added diagnostic log message to track Ethernet/IP stack memory usage.
MYNAH Technologies LLC
390 South Woods Mill Road, Suite 100
Chesterfield, MO 63017 USA
© MYNAH Technologies 2012 - 2020. All rights reserved.
Designs are marks of MYNAH Technologies, Emerson Process Management, DeltaV, and the DeltaV design are marks of one of the Emerson Process Management of companies. All other marks are property of their respective owners. The contents of this publication are presented for informational purposes only, and while every effort has been made to ensure their accuracy, they are not to be construed as warrantees or guarantees, expressed or implied, regarding the products or services described herein or their use or applicability. All sales are governed by our terms and conditions, which are available on request. We reserve the right to modify or improve the design or specification of such products at any time without notice.
While this information is presented in good faith and believed to be accurate, Mynah Technologies does not guarantee satisfactory results from reliance upon such information. Nothing contained herein is to be construed as a warranty or guarantee, express or implied, regarding the performance, merchantability, fitness or any other matter with respect to the products, nor as a recommendation to use any product or process in conflict with any patent. Mynah Technologies reserves the right, without notice, to alter or improve the designs or specifications of the products described herein.