These release notes are for the ModbusTCP VIM2 firmware v4.5.2. Previous released driver is v4.5.1. The flash procedure is documented in the product manual.
If upgrading the VIM2 from firmware v4.2.0 or earlier, follow the procedure below:
If upgrading the VIM2 from simulation firmware v2.5.4 or earlier, follow the two step procedure below:
Note that when flashing the firmware to v4.5.2 from any version prior to v4.4.1, the VIM will decommission itself. This is due to the device database size change in the VIM.
*Contact Mynah Technologies Technical Support to get Simulation firmware v2.5.5.
Mandatory for all Modbus TCP VIM2 installations using firmware v4.4.0 through v4.5.1, with applications which communicate with Quantum HSBY (Hot Standby) systems. Users with simplex devices, or other redundancy architectures (i.e., non Quantum HSBY chassis) are not impacted.
Recommended for all other users.
Quantum redundancy with hot standby chassis employs switching IP addresses where the active PLC chassis always has the same Primary IP address and the standby PLC chassis always has the same Secondary IP address. On chassis switchover, the IP addresses also switch, and the new active PLC chassis assumes the primary IP address. Consequently, communications with the VIMs always use the same Primary IP address.
In this architecture, a Quantum PLC is usually configured as a redundant device with option “Redundancy with Switching IP” in VIMNet Explorer, as shown below:
This functionality is defective in the affected firmware versions.
When “Redundancy with Switching IP” is configured, the active VIM is expected to always communicate with the PLC active chassis Primary IP address. MYNAH Technologies has confirmed this defect where the active VIM is incorrectly sending read/ write commands to the Secondary IP address (which corresponds to the inactive chassis). The Secondary IP responds to the read/write requests normally and so no issue will be detected in DeltaV. When a write message is sent, the Secondary IP will acknowledge the write but will not update the provided register, resulting in “silent” write failures in DeltaV.
This defect has been corrected in this firmware version, v4.5.2.
390 South Woods Mill Road, Suite 100
Chesterfield, MO 63017
MYNAH Technologies LLC
390 South Woods Mill Road, Suite 100
Chesterfield, MO 63017 USA
© MYNAH Technologies 2012 - 2020. All rights reserved.
Designs are marks of MYNAH Technologies, Emerson Process Management, DeltaV, and the DeltaV design are marks of one of the Emerson Process Management of companies. All other marks are property of their respective owners. The contents of this publication are presented for informational purposes only, and while every effort has been made to ensure their accuracy, they are not to be construed as warrantees or guarantees, expressed or implied, regarding the products or services described herein or their use or applicability. All sales are governed by our terms and conditions, which are available on request. We reserve the right to modify or improve the design or specification of such products at any time without notice.
While this information is presented in good faith and believed to be accurate, Mynah Technologies does not guarantee satisfactory results from reliance upon such information. Nothing contained herein is to be construed as a warranty or guarantee, express or implied, regarding the performance, merchantability, fitness or any other matter with respect to the products, nor as a recommendation to use any product or process in conflict with any patent. Mynah Technologies reserves the right, without notice, to alter or improve the designs or specifications of the products described herein.