These release notes are for the VimNet Explorer Utility version 22.214.171.124. The previous version is 126.96.36.199
Corrected ODVA FHX export. Added FHX definition of Mynah DeviceNet Device definition (EDS) file to FHX Export (as option). Added Mynah_ODVA.EDS file to VimNet Explorer Installation.
VIM1 Flash does not work under Windows 10 due to a short network timeout. Created a default timeout of 4095 ms and stored as FlashTO in CURRENT_USER\Software\Mynah Technologies\PPV\Settings registry entry. This corrects flash timeout issues with versions of Modbus firmware with sleep time of 1000ms following flash mode request.
Corrected ODVA Redundancy checkbox in registry which was not enabled by default.
Modified need for CMM files to be read from the BIN folder. Instead, use Application Data (UserDir in registry) as source.
Corrected CMM mapping where wrong Modbus Address (199) is mapped to Dataset
Modifications for FMC Firmware (VIM2) allowing output only datasets for DO setpoint value and AO setpoint mode includes ability to configure status read-back (field status) as 32-bit with high 16-bit word replacing AO and DO setpoint (value/mode) high 16-bit word read-back of output write status.
Added Long File Type (L) for read/write access to 32-bit integers in ControlLogix and Micrologix DF1 definitions. This capability is available when using SLC_TYPED_LOGICAL access.
Added Output and Input File type read/write access for Micrologix DF1 definitions. This capability is available when using SLC_TYPED_LOGICAL access.
Corrected Dataset tab in DF1 definition. Changed INT16 dataset number of bytes from 100 to 200 (100 registers), and sets UINT8 to 100 bytes (100 registers).
Allow name and tag editing of ODVA DeviceNet signal instances.
Corrected item sorting in the ProfinetLogBook dialog. The items are now sorted chronologically by default. You can sort by any column. When new items are added, the list does not return to the top.
Track “Logging to:” in VimNet Diagnostic for all firmware types to correctly enable/disable logging. Fixed data race condition where Diagnostics would sometimes not start the thread required to poll data from the VIM.
Allow modification of logging port number in PIOLog (in properties dialog).
Fixed an occasional crash in Diagnostics.
390 South Woods Mill Road, Suite 100
Chesterfield, MO 63017
MYNAH Technologies LLC
390 South Woods Mill Road, Suite 100
Chesterfield, MO 63017 USA
© MYNAH Technologies 2012 - 2019. All rights reserved.
Designs are marks of MYNAH Technologies, Emerson Process Management, DeltaV, and the DeltaV design are marks of one of the Emerson Process Management of companies. All other marks are property of their respective owners. The contents of this publication are presented for informational purposes only, and while every effort has been made to ensure their accuracy, they are not to be construed as warrantees or guarantees, expressed or implied, regarding the products or services described herein or their use or applicability. All sales are governed by our terms and conditions, which are available on request. We reserve the right to modify or improve the design or specification of such products at any time without notice.
While this information is presented in good faith and believed to be accurate, Mynah Technologies does not guarantee satisfactory results from reliance upon such information. Nothing contained herein is to be construed as a warranty or guarantee, express or implied, regarding the performance, merchantability, fitness or any other matter with respect to the products, nor as a recommendation to use any product or process in conflict with any patent. Mynah Technologies reserves the right, without notice, to alter or improve the designs or specifications of the products described herein.